UA/UB/UC-TYPE (BURIED TYPE)
New material pollution water tank – KS F 4814 Polyethylene water tank
▷ TANK COLOR
－ BASIC : Blue
> Please contact us when ordering other than the basic color.
▷ Introduction of item
－ Newell Tank is the first brand in the domestic water tank industry and is the unique brand of the Isle resin industry water tank which is certified as “KS F 4814 Polyethylene water tank”.
－ Newell Tank is a specially designed special polyethylene water tank based on pollution-free raw material and accumulated excellent technology so that clean and pure water can be used in every household, agricultural irrigation facility and industrial field throughout. It is light and has excellent impact resistance, It is manufactured by integral method and there is no leakage.
－ The KS marked products are responsible for the quality and post-issue by the government, and our KS certified production plants are responding to customers’ demands with thorough production and quality control in accordance with applicable industry standards and certification standards.
－ The development of 40 tons of new product and 50 tons of newell tank (water tank) has satisfied customers’ need for tank enlargement.
▷ Product Features
－ As a buried tank, space can be utilized widely.
－ It is easy to handle and construction because it is made of one piece made of polyethylene with excellent pressure resistance and impact resistance.
－ It is not corroded by various kinds of chemicals, and is also excellent in heat resistance (~ 70 ℃) and cold resistance (~ -50 ℃).
▷ Product Usage
> Storage of water
－ Industrial use
> Drain tank
▷ Product Specification and Specification
▷ Product drawing
▷ Construction method
> In wet or watery soil, do not install as much as possible, but in places where water comes out, pull out the water with a pump
> It should be installed at a distance of 2M or more from a building or parking lot. If it is next to a building or parking lot, install a retaining wall after installation
－ Floor foundation work
> The foundation of the floor should be more than 50cm larger than the landfill tanks and more than 200mm of concrete such as cement, gravel etc.
－ Water filling
> Fill the tank with 2/3 or more water to fix the tank and piping.
> When installing piping, be sure to install AIR VENT at the top.
> Do not remove the water until the tank is buried and the loaded soil is fixed and stabilized.
> If you do not use for a long time, please be sure to fill the water.
* Caution: Take measures to prevent freezing of winter water.
－ Back Filling
> When backfilling, use fine sand, stone, and sand as much as possible.
> Please be sure to crush the coarse soil.
> Do not use sand or gravel alone to avoid flooding.
> Large concrete, softened, stone, wood, etc. Please be sure to remove the lumps.
> Make sure there is enough space around the tank and no voids.
> If there is a large amount of sand, please clog the sand.
－ Precautions for UC-Type landfill construction (related to piping)
> It is recommended to process the upper part when piping piping connection. When processing the bottom of the tank or side piping, pipe line connecting with the starting point of nozzle piping must be unexposed to the soil. Concrete box or retaining wall must be installed separately to prevent earth pressure.
－ Notes after burial
> Do not install structures with large loads on top of the buried tanks.
> Take measures to prevent danger such as coming close, and to install protection against large-scale installation.
> Do not store any liquid other than water.
－ A must read
> We must observe all the above points during construction and we will not be liable for A / S and compensation in advance for any problems caused by non-conformity.